||Backflow Prevention Device, Wh
||mop sink faucet
||Found a y type shutoff valve installed downstream of the mop sink with an atmospheric vacuum breaker on the faucet. To correct either remove y type shutoff, as shutoff valves are not allowed downstream of an atmospheric vacuum breaker or install a hose bibb vacuum breaker downstream of shutoff valve. ,
||Manual and Mechanical Warewash
||Chlorine solution concentration
||Below 50 ppm
||Used a chlorine test kit and found the dishwashing machine not chlorine sanitizing dishes. Pic has called for repair, and has been instructed to use the 3 compartment sink to wash, rinse and sanitize dishes. ,
||Equipment Food-Contact Surface
||Food-contact surface(s) used for nonpotentially hazardous food(s) beverage dispensing nozzles
||counter top(s) pop gun
||Found slight accumulation in the pop gun nozzle in the center of the bar. To correct follow manufacturer's directions and clean pop nozzle.
||Good Repair and Proper Adjustm
||wait station handsink
||In poor repair
||Found the paper towel dispenser in the kitchen waitstation broken and not working, but paper towels available. Found the left ice machine in the kitchen not working. Found the left fan in the evaporator coil of the beer walk in cooler not working. To correct repair paper towel dispenser, ice machine and walk in cooler fan.
||Nonfood contact surface(s)
||cooking area hood
||Found the hood filters, edges and some surfaces of hoods soiled with grease and dust. Found some door gaskets of cooler soiled with accumulation, and the bottom of some coolers with pooling water. Found the exterior surfaces and and edges of ovens soiled with accumulation. To correct clean hood filters, hood surfaces, door gaskets, coolers and ovens
||System Maintained in Good Repa
||Plumbing system Drain line(s)
||ice bin drain lines
||Found the drain line of the ice bin in the bar missing and water dripping on the floor. To correct repair/replace drain line and ensure the drain line is at least 1 inch above the rim of the floor drain.
||In-Use Utensils, Between-Use S
||ice bin pop gun
||Improperly stored With handle in product
||Found the handle of ice scoops in several ice bins in facility stored on top of ice. To correct store ice scoops with handles up or in a container/holder. Found the pop guns in the waitstation by the bar laying on top of ice in the ice bin. To correct securely place pop guns in holder.
||Lighting intensity at work levels
||cooking area hood
||Less than 50 foot candles
||Found 1 light in the cooking hood not working. Found the lights in the walk in freezer blinking and dim. To correct repair/replace lights in hood and in the walk in freezer