Health Report #106487
Chela's Restaurant & Taqueria (South)
||Backflow/backsiphonage prevention device(s) Air gap
||ice machine drain lines
||Not provided on Ice machine
||Found the drain line of the ice machine draining directly into an end plug of a drain line without air gap. To correct provide an air gap of at least 1 inch from the end of the ice machine drain line and the rim of the drain line.
||Found an unsealed wood stand used under the ice machine. To correct either replace wood stand with a stainless steel equipment stand or seal wood stand to be nonabsorbent.
||Physical facilities Floor(s)
||front counter area floor
||In poor repair
||Observed gaps along the wall and floor around the front counter area. To correct fill gaps to be durable, smooth and cleanable.