1497 Ecorse Road
Ypsilanti, MI 48197
This incident (43849) does not have any more information on it
(Critical) There is some kind of a device on top of the hot water that may be a pump. There is a discharge line to the outside and a drainline from the tank that is submerged into the mop sink with a flex tubing that terminates inside the mop sink basin. There must be an air gap between the end of the drainline and the top rim of the mop sink to minimize potential for backsiphonage of sewage into the water tank. In addition there is an overflow flex drainline from the line that discharges to the outside of the building. This flex tubing needs to be cut so that it is airgapped above the top rim of the mopsink also. Health dept will review the photos taken to confirm that these drainlines need to be airgapped. Contact landlord to repair as indicated above.
This incident (33372) does not have any more information on it
This incident (43851) does not have any more information on it